Wireless Thermostat with Occupancy Sensor
BEFORE YOU BEGIN DETERMINE THE APPROPRIATE INSTALLATION LOCATION FOR THE THERMOSTAT. THE THERMOSTAT SHOULD FACE THE BED AREA OF THE ROOM.
After the installation, follow the “Thermostat Configuration” Instructions to correctly configure the thermostat.
For installation of a networking thermostat with remote management, refer to the “Network Installation” manual.
BEFORE YOU BEGIN: Consult PTAC manufacturer’s documentation or use a voltmeter to determine if the PTAC unit outputs AC or DC power (24V).
If the PTAC unit outputs AC power, make sure that the jumper on the Wireless Control Card is in the AC position – jumper is connecting “R” and “COM” pins (Default).
If the PTAC unit outputs DC power, make sure that the jumper on the Wireless Control Card is in the DC position – jumper is connecting “COM” and “C” pins.
Installing the Wireless Control Card
➤➤ Unplug the PTAC unit power cord from the electrical outlet;
➤➤ Remove the PTAC cover;
➤➤ Set the PTAC unit to “External Thermostat” (Class 2) mode.
Consult the PTAC unit documentation to determine how to set the PTAC unit to “External Thermostat” mode.
➤➤ Connect the wires to screw terminals on the PTAC unit – refer to the Wiring Table to determine proper connections.
➤➤ Mount the control card inside of the PTAC unit.
Make sure that the Wireless Control Card antenna is not touching any metal components of the PTAC unit. Make sure that the contol card is not and cannot fall into the PTAC unit Condensation Pan.
➤➤ Replace the PTAC front cover;
➤➤ Plug in the PTAC unit power cord into an electrical outlet.
Questions about your Verdant Thermostat Manual VX Model? Post in the comments! Download User Manual [PDF]