HEAT WALL ORGANIZERS Repurposeful Instructions Give your old IKEA items new life. DIFFICULTY LEVEL: BEGINNER #IKEAinspo ORIGINAL PRODUCT:…
MRXBOXAB-ECO3B-AESW (Standard Hand Unit)
MRXBOXAB-ECO3B-AEHSW (Opposite Hand Unit)
MRXBOXAB-ECO5B-AESC (Standard Hand Unit)
MRXBOXAB-ECO5B-AEHSC (Opposite Hand Unit)
MRXBOXAB-ECO5B-AESW (Standard Hand Unit)
MRXBOXAB-ECO5B-AEHSW (Opposite Hand Unit)
Mechanical Ventilation Units with Heat Recovery for Wall Mounting
Read and understand the installation and maintenance manual before installing, operating or maintaining this product.
This manual contains important information on the safe and appropriate assembly, transport, commissioning, operation, maintenance, disassembly and simple troubleshooting of the product. While the product has been manufactured according to the accepted rules of current technology, there is still a danger of personal injury or damage to equipment if the following general safety instructions and the warnings contained in these instructions are not complied with.
The following minimum Personal Protective Equipment (PPE) is recommended when interacting with Nuaire product:
The ECO(3/5)B-AE wall mounted range of units are designed to offer improved sound levels and an aesthetically pleasing installation by housing a Mechanical Ventilation with Heat Recovery unit (MVHR) and attenuator inside an acoustically lined enclosure. The MVHR unit is fitted with two independent fans. Each fan has full speed control for background and boost ventilation rates. To recover heat from the extract air the heat exchanger block is utilised. The heat exchanger can recover up to 95% of the normally wasted heat. Bypass operation can be disabled via a manual switch in colder months so the unit recovers heat continually.
Installation must be carried out by competent personnel in accordance with the appropriate authority and conforming to all statutory governing regulations. All mains wiring must be in accordance with the current I.E.E. Regulations, or the appropriate standards. Ensure that the mains supply (Voltage, Frequency and Phase) complies with the rating
Please allow a minimum of 360m in front of an
The fan must be installed indoors, on a suitable wall away from direct sources of frost, heat and water spray or moisture generation. For a vibration-free result the unit must be mounted to a solid wall.
The unit must remain switched on at all times to maintain ventilation within the dwelling. Turning the unit off will cause long term damage to the unit and building fabric.
To prevent damage during transportation the product is shipped with securing fixings, these can be found front and centre of the enclosure top panel (Figure 3). These must be removed before use, failure to do so will result in excessive vibration and noise. The screws removed can be discarded and replaced with rubber caps provided.
The unit is designed for wall mounting on a solid wall only, a gypsum block/plasterboard wall will not suffice.
Examples of suitable installation are shown overleaf. The wall brackets supplied should be secured to the wall using suitable fixings (supplied by others) as per the dimensions given in figure 4. The head of the chosen fixing should protrude no more than 8mm from the wall bracket. The enclosure assembly can then be lifted using suitable equipment and moved into position so it is sitting directly on the wall brackets (ensuring the rear panel of the enclosure is not in contact with the wall bracket fixings). The enclosure can be secured to the wall brackets using the 4x M8 fixings supplied.
No part of enclosure should be in contact with the building structure, the only components that should be in contact are the wall mounting brackets.
Care must be taken to ensure the unit is installed true in all 3 dimensions. Failure to do so may result in overflow from the internal condensation drip tray.
The MVHR unit fixed to a solid wall construction using the mounting bracket provided.
If it is not practical to use a solid wall, the MVHR unit should be fixed to a stud partition with a 25mm minimum thickness MDF panel solidly fixed behind the plasterboard.
If fixing to a stud wall the MDF panel should extend, width wise, over a minimum of 3 vertical studs with centres of no more than 400mm. Add additional vertical supports if necessary.
Height wise, ideally, the MDF panel should extend from floor to ceiling but as a minimum should be a least 2m high.
Fix the mounting bracket to the wall (Figure 3) and use the wall mounted bracket to mount the unit on (Figure 5).
The MVHR unit inside the enclosure is fitted with a straight coupling to allow 21.5mm overflow pipe (not supplied) to be attached using solvent cement, the pipe should be passed through the flexible adhesive backed cover plate before the solvent cement is applied.
The pipe can then be inserted into the coupling of the MVHR unit and the cover plate slid along the length to bond against the base panel of the enclosure preventing noise breakout (Figure 7).
The condensate must be discharged under a water level in a U-trap drainpipe or an alternative drain method which acts as an airlock. This condensate discharge connection is suitable for 21.5mm Ø overflow pipe. Solvent cement should be used to make the joint.
If using a U-trap please ensure the U-trap has been filled to a suitable level of water to avoid any air locks. If the condensation pipe is fitted in an unheated space the pipe should be in insulated to prevent freezing.
An MVHR-DRAIN is recommended for use as the primary condensate take-off (Figures 8 and 9).
The unit is designed to extract air from all wet rooms e.g. bathroom, kitchen, en-suite, utility room (with sink). WC’s do not need to be ventilated if openable windows are fitted.
Supply air should be to all habitable rooms e.g. bedrooms and lounge.
Extract/input grilles should be adjustable valve types (not supplied).
External grilles are to have a minimum free area of 12,250 sq. mm.
Before commencing ducting installation reference should be made to building regulations document “Domestic ventilation compliance guide”. This document supports ADF2010 and details installation, testing and commissioning of all ventilation systems.
It is recommended that rigid ducting be used at all times. Flexible ducting has a very high resistance and it is impossible to calculate how much resistance will be on a system if used.
If used the flexible ducting must be kept to a minimum and should always be pulled taut. A maximum of 300mm should be used on each leg.
To prevent condensation on the outside of the outside air inlet duct and the air outlet duct from the unit, these ducts should be insulated.
Ducting must be installed in such a way that resistance to airflow is minimised. Bends should be kept to a minimum.
A minimum distance of 300mm between the appliance and any bends in ductwork is recommended.
Ideally 150mm diameter or 204 x 60mm rectangular ducting should be used (Figures 12 & 13).
Ducting joints must be sealed with silicone type sealant and shall be adequately and reliably fixed to the appliance.
|ADF 2010 – Extract Ventilation Rates|
|Room||Minimum High rate||Minimum Low Rate|
|Kitchen||13 l/s||Total extract rate should be at least |
the whole dwelling ventilation rate given in table 2.
|Utility Room||8 l/s|
|Whole Dwelling Ventilation Rates|
|Whole dwelling |
|Number Of Bedrooms In Dwelling|
Any air intake terminal must be installed in accordance with the appropriate regulation. As a guide, the BS5440 series of British Standards deals with this issue and currently states that an air intake must be at a minimum distance of 300mm from a gas boiler balanced flue. Installers are advised to be aware of the requirements of this standard when installing ‘through the wall’ supply air ducting.
The MVHR system has been sized for the winter period. Additional ventilation may be required during the warmer months and it has been assumed that the provisions for purge ventilation (e.g. openable windows) could be used.
Step 1: For any design air permeability, determine the whole dwelling ventilation supply rate from Whole Dwelling Ventilation Rates table.
As an alternative where the design air permeability is intended to be more than (>) 5m3/(h.m2) 50 Pa, allow for infiltration for all dwelling types by subtracting from the whole dwelling ventilation supply rate from Whole Dwelling Ventilation Rates table; 0.04 x gross internal volume of the dwelling heated space (m3).
Step 2: Calculate the whole dwelling extract ventilation rate by summing the individual room rates for ‘minimum high rate’ from ADF 2010 – Extract Ventilation Rates table.
(For sanitary accommodation only, as an alternative, the purge ventilation provisions given in ADF 2010 can be used where security is not an issue. In this case ‘minimum high extract rate’ for the sanitary accommodation should be omitted from the step 2 calculation).
Step 3: The required airflow rates are as follows:
For Scotland refer to BRE Digest 398.
For further information refer to “Domestic Ventilation Compliance Guide” www.planningportal.gov.uk/buildingregulations/approved documents/partl/compliance.
MRXBOX units are designed to ventilate the whole dwelling and must not be used during site construction or the clean-up period. Cement and plaster dust can be abrasive and can affect fan performance and reliability. Please ensure that the filters are checked prior to commissioning to ensure there is no build-up of dust or debris.
While the property is drying out, very high moisture levels are likely to occur. Therefore it is advisable that if the installation and building works are complete the unit is left running. If the building works are not complete please close the air valves or cover up the air valves to prevent condensation forming in the ductwork and the MRXBOX unit due to natural migration of warm air.
11. Unit Dimensions
UNI T WEI GHT = 56Kg
If ancillary distribution box (DB-ECO3) is to be used refer to documentation supplied with DB-ECO3 for additional infomation as requirements will differ.
ALSO FROM NUAIRE –
(see installation document 671780)
For good EMC engineering practice, any sensor cables or switched live cables should not be placed within 50mm of other cables or on the same metal cable tray as other cables.
The electrical connection of the unit must be carried out by a qualified electrician. The unit is supplied with a flexible cord for connection to the mains supply.
Voltage: 240V 1ph 50Hz
This unit must be earthed.
The cable from the mains power supply should be connected to a fixed wiring installation, via a fused isolator, in accordance with current IEE wiring regulations.
The filters fitted inside the unit are protected with a plastic film.
Prior to commissioning remove the covers (Figure 20), take off the film and replace.
This product contains an internal humidity sensor fitted into the airflow extracting from the wet rooms. When the unit senses that the humidity exceeds the set point the unit will boost to that set by the commissioned boost speed. The set point can be found behind the front of the unit (Figure 18) and is at its least sensitive when turned fully clockwise. Note that the sensor is measuring humidity from all the wet rooms at the same time and should not be relied on to solely boost the unit. Additional switch should be used local to the wet rooms (Section 4.2).
Adjustment only to be carried out by qualified person, isolate power before removing cover.
The status of the unit is indicated by a series of LED’s on the front cover.
The variants are listed below.
The display on the unit control panel will not indicate when a higher speed setting has been triggered by an external source.
Intake and extract temperatures are monitored at the point the airflows enter the unit, if the range falls within the set parameters the bypass damper is opened automatically to target an indoor comfort temperature all year round.
The extract temperature is an average from all wet rooms. If this exceeds 25°C the unit may go into bypass depending on outside temperatures.
When the switch position is set to Summer the integral automatic summer bypass is fully operational, in the alternative Winter position the HX bypass is disabled to ensure the unit is constantly in heat recovery mode.
Speed 3 will be non-operational if the intake temperature is greater than the extract temperature.
In the event of the intake air temperature at the unit dropping below the predetermined set point (-5°C as standard) the supply fan will reduce to minimum speed, once the temperature rises above the set point the fan will return to its commissioned speed.
Frost protection will only activate after ten days of continuous run time. If commissioning of the unit is outside of this time frame please notify the after sales department prior to site visit.
It is important that maintenance checks are recorded and that the schedule is always adhered to, in all cases, the previous report should be referred to.
Filters are to be inspected every 6 months and replaced every 12 months (or sooner if required). Failure to do so may impair the performance and energy efficiency of this unit. A flashing LED (Section 5.2) will indicate that a filter change is required. This indication repeats every 12 months and will turn off automatically after 5 Days.
Remove the filter covers on the front panel of the unit by gripping the two circular tabs either end of the filter covers and pulling away from the unit. The filter can now be extracted by pulling the black removal loop on the front edge of the filter. Once the filters have been inspected return or replace them as necessary.
The 5 year warranty starts from the day of delivery and includes parts and labour for the first year. The remaining period covers replacement parts only.
This warranty is void if the equipment is modified without authorisation, is incorrectly applied, misused, disassembled, or not installed, commissioned and maintained in accordance with the details contained in this manual and general good practice.
The product warranty applies to the UK mainland and in accordance with Clause 14 of our Conditions of Sale. Customers purchasing from outside of the UK should contact Nuaire International Sales office for further details.
Failure to maintain the unit as recommended will invalidate the warranty.
Where possible Nuaire use components which can be largely recycled when the product reaches its end-of-life:
Ensure that Nuaire product is made safe from any electrical / water/refrigerant supplies before dismantling commences. This work should only be undertaken by a qualified person in accordance with local authority regulations and guidelines, taking into account all site based risks.
For technical assistance or further product information, including spare parts and replacement components, please contact the After Sales Department.
If ordering spares please quote the serial number of the unit together with the part number, if the part number is not known please give a full description of the part required. The serial number will be found on the identification plate attached to the unit casing.
Telephone 02920 858 400
Technical or commercial considerations may, from time to time, make it necessary to alter the design, performance and dimensions of equipment and the right is reserved to make such changes without prior notice.
Nuaire | Western Industrial Estate | Caerphilly | CF83 1NA | nuaire.co.uk
19. 11. 21. Document Number 672008
|nuaire MRXBOXAB-ECO3B-AESW Mechanical Ventilation Units with Heat Recovery for Wall Mounting [pdf] Instruction Manual|
MRXBOXAB-ECO3B-AESW, MRXBOXAB-ECO3B-AEHSW, MRXBOXAB-ECO5B-AESC, Mechanical Ventilation Units with Heat Recovery for Wall Mounting
XCover 5 5-Slot Charging Cradle for XCover Pro Charging via USB Type-C Use a genuine…
IN03E Wireless Door Stop Alarm door stop alarm instruction sheet Please keep these instructions in…
239604 Pasadena Wall Bracket Installation Instructions PASADENA WALL BRACKET SKU# 239604, 239605 Rated Voltage 220-240V~…
PLUTV55BTR 5.25 Inch Waterproof Rated Off Road Wireless BT Speakers What's in the Box: ·…
KB310-SSWM Surface Mounted Baby Changing Station Koala Kare Products Installation & Operations Instructions KB310-SSWM Surface-Mounted…
SR1000 Wireless Transmitter SDB SR1000 Wireless Transmitter T: 0031-(0)85 732 68 59 | E: firstname.lastname@example.org…