User Guide for Honeywell models including: Y87RFC, Connected Single Zone Thermostat
2 Connected Single one Thermostat uick Start Guide Preparation Before installation Check that the thermostat is compatible with your boiler. Refer to the boiler manufacturerâ€™s instructions.
File Info : application/pdf, 12 Pages, 1,001.81KBDocumentDocument
Y87RFC Connected Single Zone Thermostat EN Quick Start Guide Installation in 3 steps 1 2 1 3 Install the Thermostat and Boiler Relay Install the Internet Gateway Get Connected 2 Preparation Before installation Check that the thermostat is compatible with your boiler. Refer to the boiler manufacturer's instructions. The wireless thermostat can be located almost anywhere you wish; see diagrams for guidance on the ideal location. As it requires no wires it makes the installation very simple. Before installing the Boiler Relay, ensure the mains power to the boiler is switched off. During installation You will need the following: Cross-head screwdriver Small flat blade screwdriver Pliers Wire-strippers After installation Dispose of any old electronic equipment at an authorised recycling centre. Connected Single Zone Thermostat Quick Start Guide Avoid draughts Do not locate above a source of heat 1.2 - 1.5m Do not locate in direct sunlight Locate 1.2 - 1.5m from the floor 3 Step 1 : Install the Thermostat and Boiler Relay 1. If necessary, disconnect and remove the old equipment. Attention! This thermostat does not require any wiring. Isolate any conductors and reposition them inside the wall. . 2. Separate the thermostat from the mounting plate. Remove the setpoint dial Press down on the top of the thermostat and hinge it downwards 3. Attach the mounting plate to the wall. Plugs 4. Reattach the thermostat to the mounting plate Hook the thermostat hinges into the base of the mounting plate Screws Remove the tab from between the batteries Hinge the thermostat upwards and click into place Replace the setpoint dial 4 Step 1 b : Install the Thermostat and Boiler Relay 5. Remove the wiring plate from the Boiler Relay. 6. Mount the wiring plate to the wall. Use a screwdriver to unclip the cover from base. 7. Wiring the Boiler Relay Hinge the cover upwards to remove. Blue Brown Refer to the boiler installation guide for instructions on wiring the Boiler Relay to the correct terminals in the boiler. Wire N and L to neutral and live. Connected Single Zone Thermostat Quick Start Guide Mount on a plastic wallbox or directly on the wall next to the boiler. For best RF performance keep a distance of at least 30cm from the boiler, other metal objects or mains cables. 8. Attach the Boiler Relay to the wiring plate. Locate hinges, rotate the cover downwards and click into place. Reconnect the mains power to the installation. 5 Step 2 : Install the Internet Gateway RFG100 1. Connect the Gateway to a mains power source. During power up the 3 LEDs will light up red. The power and RF communication LEDs should then change to green - indicating that the Gateway is powered and successfully connected to the Thermostat. 2. Connect the Gateway to an internet router with the provided Ethernet cable. The connectivity LED should begin to flash green - indicating that the Gateway has successfully connected to the internet (but not yet registered) 6 Step 3 : Get Connected 1. Create an account online. Visit the website below and follow the steps to create an account. getconnected.honeywellhome.com 2. Name your location. After creating an account and receiving the activation confirmation e-mail, choose a suitable name for the location of the thermostat (e.g. My Home). Connected Single Zone Thermostat Quick Start Guide New graphic needed 7 Step 3 : Get Connected 3. Register the Internet Gateway. Enter the MAC and CRC codes of your Internet Gateway 4. Download the Smartphone App The MAC and CRC codes are on the information label on the bottom of the Gateway. 5. Use the app The green LED will stop flashing when the Internet Gateway has been successfully registered. Download the "Total Connect Comfort International" App for your Smartphone or Tablet. Log in to the App and start controlling your heating remotely, or setting up a heating schedule for each day of the week. 8 Error Messages Loss of RF communication O with the Gateway Loss of RF communication with the Thermostat No internet connection Connecting to the router Gateway not yet registered Cycle the power to the Gateway and verify that it is located within the RF communication limits of the thermostat. Check the RF thermostat is powered and is within RF range. Check the router has access to the internet. If the LED stays orange, check the cables and power supply to the router. Create an account and register the Internet Gateway on: getconnected.honeywellhome.com Note : RF communication can be affected by obstacles, metal objects or excessive distance between the RF devices. It may be necessary to reposition devices for better performance if the RF communication seems unreliable. Connected Single Zone Thermostat Quick Start Guide For support: Resideo 200 Berkshire Place Winnersh Triangle, Berkshire RG41 5R Phone: 0300 130 1299 Pittway Sarl, Z.A. La Pièce 4, 1180 Rolle, Switzerland Country of origin : UK © 2020 Resideo Technologies, Inc. All rights reserved. The Honeywell Home trademark is used under license from Honeywell International Inc. This product is manufactured by Resideo Technologies, Inc. and its affiliates. 32300956-012 B