Kidde KN-COPP-3 Carbon Monoxide Alarm
ATTENTION: Please take a few minutes to thoroughly read this user’s guide which should be saved for future reference and passed on to any subsequent owner.
What to do When the Alarm Sounds!
Carbon Monoxide Alarm Procedure
WARNING: Activation of the CO Alarm indicates the presence of Carbon Monoxide (CO) which can kill you.
- Operate the Test/Reset button;
- Call your emergency services (Fire Department or 911); PHONE NUMBER:
- Immediately move to fresh air – outdoors or by an open
door/window. Do a head count to check that all persons are accounted for. Do not reenter the premises nor move away from the open door/window until the emergency services responders have arrived, the premises have been aired out, and your alarm remains in its normal condition.
- After following steps 1-3, if the alarm reactivates within a 24 hour period, repeat steps 1-3 and call a qualified appliance technician to investigate sources of CO from fuel burning equipment and appliances, and to inspect for proper operation of equipment.
If problems are identified during this inspection, have the equip-ment serviced immediately. Note any combustion equipment not inspected by the technician and consult the manufacturer’s instruc-tions, or contact the manufacturer’s directly for more information about CO safety and the equipment. Make sure that motor vehicles are not, or have not been, operating in a garage attached or adja-cent to the residence.
Never restart the source of a CO problem until it has been corrected. Never ignore the sound of the alarm!
If the alarm is sounding, pressing the test/reset button will terminate the alarm. If the CO condition that caused the alert in the first place continues, the alarm will reactivate. If the unit alarms again within six minutes, it is sensing high levels of CO which can quickly become a dangerous situation.
welcome note: Many times throughout this User’s Guide, we will refer to Carbon Monoxide as “CO”.
This Kidde carbon monoxide (CO) alarm is an important part of your family’s home safety plan. This alarm has been designed and tested to detect CO buildup in a residential environment. Your alarm is for use specifically in the home. As an owner of a CO alarm, there are some basic facts you should know about for your protection.
Many people think that CO alarms operate like smoke alarms. Like smoke alarms, CO alarms monitor the air in your home and sound a loud alarm to warn you of trouble. The way you respond to a CO alarm is quite different than a smoke alarm. That’s because a house fire and a CO problem are two distinctly different situations. If your smoke alarm were to alarm, you would quickly be able to judge the level of danger you were in with your senses. You can see and smell the smoke, feel the heat, see, and possibly hear the fire burning. You can also readily see if your smoke alarm is alarming in a non-emergency situation. Because your sense of sight, smell, hearing and touch give you information, you can almost instantly judge what action to take if you hear your smoke alarm.
CO is an invisible, odorless, tasteless and non-irritating gas – completely undetectable to your senses. That’s why it is important to your safety that you have a CO alarm.
Important Warning Statements
IMPORTANT: This carbon monoxide alarm is designed to detect carbon monoxide from ANY source of combustion. It is NOT designed to detect smoke, fire, or any other gas.
! WARNING: Carbon monoxide alarms are not smoke alarms. This carbon monoxide alarm is not a substitute for installing and maintaining an appropriate number of smoke alarms in your home.
This carbon monoxide alarm will not sense smoke, fire, or any poisonous gas other than carbon monoxide even though carbon monoxide can be generated by fire. For this reason you must install smoke alarms to provide early warning of fire and to pro-tect you and your family from fire and its related hazards.
CAUTION: This alarm will only indicate the presence of carbon monoxide at the sensor. Carbon monoxide may be present in other areas.
! WARNING: This product is intended for use in ordinary indoor locations of family living units. It is not designed to meas-ure compliance with Occupational Safety and Health Administration (OSHA), commercial or industrial standards. It is not suitable for installation in hazardous locations as defined in the National Electric Code.
The installation of this device should not be used as a substitute for proper installation, use and maintenance of fuel burning appliances, including appropriate ventilation and exhaust sys-tems. It does not prevent CO from occurring, nor can it solve an existing CO problem.
! WARNING: This device is designed to protect individuals from acute effects of carbon monoxide exposure. It may not fully safe-guard individuals with specific medical conditions. If in doubt, consult a medical practitioner.
Individuals with medical problems may consider using warning devices which provide audible and visual signals for carbon monoxide concentrations under 30 PPM.
This carbon monoxide alarm requires a continuous supply of elec-trical power – it will not work without power. Models without battery backup will not operate during power failure.
This alarm has not been investigated for carbon monoxide detec-tion below 70 PPM.
Information About Carbon Monoxide
General Carbon Monoxide Information
Carbon monoxide is a colorless, odorless and tasteless poison gas that can be fatal when inhaled. CO inhibits the blood’s capacity to carry oxy-gen.
Periodically review this user’s guide and discuss your CO alarm emer-gency procedure with all the members of your family. Never ignore a CO alarm. A true alarm is an indication of potentially dangerous levels of CO. CO alarms are designed to alert you to the presence of CO before an emergency – before most people would experience symptoms of CO poisoning, giving you time to resolve the problem calmly.
Determine if anyone in the household is experiencing symptoms of CO poisoning. Many cases of reported CO poisoning indicate that while victims are aware they are not well, they become so disoriented they are unable to save themselves by either exiting the building or calling for assistance. Also, young children and household pets may be the first affected. You should take extra precautions to protect high-risk persons from CO exposure because they may experience ill effects from CO at levels that would not ordinarily affect a healthy adult.
Symptoms of CO Poisoning
The following common symptoms are related to CO poisoning and should be discussed with ALL members of the household.
Slight headache, nausea, vomiting, fatigue (often described as “flu-like” symptoms).
Severe throbbing headache, drowsiness, confusion, fast heart rate.
Unconsciousness, convulsions, cardio-respiratory failure, death.
If you experience even mild symptoms of CO poisoning, consult your doctor immediately!
Carbon Monoxide PPM Levels
Model KN-COPP-3 is equipped with a digital display that shows levels of CO (displayed in PPM – parts per million). Learn the difference between dangerous, high, mid and low levels.
When someone is experiencing symptoms of CO poisoning and CO readings are generally above 100 PPM. Anytime someone is experiencing the symptoms of CO poisoning this should be treated as an emergency. See “What to do When the Alarm Sounds” (inside front cover).
Generally above 100 PPM, with no one experiencing symptoms. This should be treated as an urgent situation. See “What to do When the Alarm Sounds” (inside front cover).
Generally between 50 PPM to 100 PPM. This should be cause for concern and should not be ignored or dismissed. See “What to do When the Alarm Sounds” (inside front cover).
Generally below 50 PPM. Kidde recommends you take action to eliminate the source of CO. See “What to do When the Alarm Sounds” (inside front cover).
Possible Sources of Carbon Monoxide
Inside your home, appliances used for heating and cooking are the most likely sources of CO. Vehicles running in attached garages can also produce dangerous levels of CO.
CO can be produced when burning any fossil fuel, such as gasoline, propane, natural gas, oil and wood. It can be produced by any fuel-burning appliance that is malfunctioning, improperly installed, or not ventilated correctly, such as:
- Automobiles, furnaces, gas ranges/stoves, gas clothes dryers, water heaters, portable fuel burning space heaters and generators, fireplaces, wood-burning stoves and certain swimming pool heaters.
- Blocked chimneys or flues, back drafts and changes in air pressure, corroded or disconnected vent pipes, loose or cracked furnace exchangers.
- Vehicles and other combustion engines running in an open or closed garage, attached or near a home.
- Burning charcoal or fuel in grills and hibachis in an enclosed area.
The following conditions can result in transient CO situations:
- Excessive spillage or reverse venting of fuel-burning appliances caused by outdoor ambient conditions, such as, wind direction and/or veloci-ty, including high gusts of wind, heavy air in the vent pipes
(cold/humid air with extended periods between cycles).
- Negative pressure resulting from the use of exhaust fans.
- Simultaneous operation of several fuel-burning appliances competing for limited internal air.
- Vent pipe connections vibrating loose from clothes dryers, furnaces, or water heaters.
- Obstructions in, or unconventional, vent pipe designs which can amplify the above situations.
- Extended operation of unvented fuel-burning devices (range, oven, fireplace, etc.).
- Temperature inversions which can trap exhaust gases near the ground.
- Vehicle idling in an open or closed garage, or near a home.
To be safe, know the possible sources of CO in your home. Keep fuel-burning appliances and their chimneys and vents in good working condi-tion. Learn the early symptoms of exposure, and if you suspect CO poi-soning, move outside to fresh air and get emergency help. Your first line of defense is an annual inspection and regular maintenance of your appliances. Contact a licensed contractor or call your local utility compa-ny for assistance.
Information About Carbon Monoxide Alarms – What They Can and Cannot Do:
CO alarms provide early warning of the presence of CO, usually before a healthy adult would experience symptoms. This early warning is possible, however, only if your CO alarm is located, installed and maintained as described in this guide.
Because carbon monoxide is a cumulative poison, long-term exposures to low levels may cause symptoms, as well as short-term exposures to high levels. This Kidde unit has a time-weighted alarm – the higher the level of CO present, the sooner the alarm will be triggered.
This CO alarm can only warn you of the presence of CO. It does not prevent CO from occurring, nor can it solve an existing CO problem. If your unit has alarmed and you’ve provided ventilation by leaving your windows and doors open, the CO buildup may have dissipated by the time help responds. Although your problem may appear to be temporarily solved, it’s crucial that the source of the CO is determined and that the appropriate repairs are made.
This CO alarm is designed to act as a monitor; it is not designed for use as a short-term testing device to perform a quick check for the presence of CO.
CO alarms have limitations. Like any other electronic device, CO alarms are not fool-proof. CO alarms have a limited operational life. You must test your CO alarm weekly, because it could fail to operate at any time.
If your CO alarm fails to test properly, or if its self-diagnostic test reveals a malfunction, immediately have the unit replaced. This alarm will not monitor CO levels while in an error condition.
CO alarms can only sense CO that reaches the unit’s sensor. It’s possible that CO may be present in other areas without reaching the alarm. The rate and ability that which CO reaches the alarm may be affected by:
- Doors or other obstructions.
- Fresh air from a vent, an open window or other source.
- CO being present on one level of the home and not reach a CO alarm installed on a different level. (For example, CO in the basement may not reach an alarm on the second level, near the bedrooms).
For these reasons, we recommend you provide complete coverage by placing a CO alarm on every level of the home. Please carefully read all information on properly installing this CO alarm.
CO alarms should not be used to detect the presence of natural gas (methane), propane, butane, or other combustible fuels.
Instruct children never to touch, unplug or otherwise interfere with the alarm. Warn children of the dangers of CO poisoning.
Product Features and Specifications
IMPORTANT: Ten (10) years after the initial power up, this alarm will “beep” two times every 30 seconds to indicate that it is time to replace the alarm. Replace the alarm immediately! It will not detect CO in this condition.
To help identify the date to replace the alarm, a label has been affixed to the side of the alarm. Write the “replace by” date (ten years from power up) in a permanent marker on this label.
Operating Range: 40°F (4.4°C) to 100°F (37.8°C)
Operating range: 10-95% non-condensing
- Audible Alarm:
85+ dB at 10’ @ 3.4±0.5 KHz pulsing alarm Sensor:
120 volts AC, 60 Hz, 60 mA max, 9 volt battery back-up
- Accuracy of Digital Display:
30-999 PPM +/-30% when measured in conditions of 80° F (+/- 10° F), atmospheric pressure +/- 10% and 40% +/- 3% relative humidity. Display readings may vary slightly depending on changes in the ambient condition (temperature, humidity) and the condition of the sensor.
- Alarm Response Times:
70 PPM = 60-240 min., 150 PPM = 10-50 min., 400 PPM = 4-15 min.
Recommended Installation Locations
CO alarms should be mounted in or near bedrooms and living areas. It is recommended that you install a Kidde CO alarm on each level of your home.
When choosing your installation locations, make sure you can hear Recommended Locations the alarm from all sleeping areas. If you install only one CO alarm in your home, install it near bedrooms, not in the basement or furnace room.
- When wall mounting, place out of reach of children. Under no cir-cumstances should children be allowed to handle the CO alarm.
- Placing the alarm at eye level allows for optimum monitoring of the digital display.
Locations To Avoid
IMPORTANT: Improper location can affect the sensitive electronic com-ponents in this alarm. To avoid causing damage to the unit, to provide optimum performance, and to prevent unnecessary nuisance alarms:
- Do not install in kitchens, garages or furnace rooms that may expose the sensor to substances that could damage or contaminate it.
- Do not install in areas where the temperature is colder than 40°F
(4.4°C) or hotter than 100°F (37.8°C) such as crawl spaces, attics, porches and garages.
- Do not install within 5 ft. of heating or cooking appliances. (Kidde recommends 15 ft. to prevent nuisance alarms).
- Do not install near vents, flues, chimneys or any forced/unforced air ventilation openings.
- Do not install near ceiling fans, doors, windows or areas directly exposed to the weather.
- Do not install in dead air spaces, such as peaks of vaulted ceilings or gabled roofs, where CO may not reach the sensor in time to provide early warning.
- Do not install on a switched or dimmer-controlled outlet.
- Do not install this unit near deep-cell large batteries. Large batteries have emissions that can cause the alarm to perform at less than opti-mum performance.
- Do not obstruct the vents located on the alarm. Do not place the alarm where drapes, furniture or other objects block the flow of air to the vents.
How to Install Your Alarm
Your Kidde CO alarm with its removable adapter allows you to install the alarm as a wall mounted unit, a direct plug unit, or as a table top unit.
In its “as shipped” configuration, all you need to do is install the 9V backup battery and your Kidde CO alarm is ready to be plugged directly into a wall socket.
Direct Plug Alarm To install:
- Choose a standard 120V unswitched outlet to plug the alarm into.
- Pull the slide support out approximately 1/4” until the slide snaps into place. This will help support unit in the wall outlet.
- Plug the alarm into the outlet.
If the outlet is mounted horizontally (side-ways): If you are going to use your alarm as a direct plug and you are going to plug in to an outlet that is mounted horizontally (sideways), you will need to rotate the adapter 90˚.
To rotate the adapter:
- Remove back door by sliding it down and out.
- Spread adapter thumb releases out and care-fully turn alarm over. This will allow adapter to slide out.
- Lift the adapter completely out of the alarm.
- Rotate the adapter 90˚ to the right (clockwise). Snap it firmly back into place.
- Carefully replace the back door. Insure the “latches” on all four cor-ners of the door are lined up, then press the door securely into place.
- Plug the alarm into an unswitched wall socket.
Wall Mounted Alarm
Installation tips for power cord models:
The power cord option provides more flexibility in mounting locations and allows the alarm to be easily installed at eye level.
For a wall-mounted unit, you will need to pull out the removable adapter and power cord.
- Follow steps 1 through 3 in the previous sec-tion under “To Rotate the Adapter.”
- With the adapter removed, pull the power cord out of the cord storage, remove the twist tie, and extend the power cord.
- With the power cord extended, press the last few inches of the power cord into the cord recess. Gently pull the cord at the bottom of the cord recess until the cord becomes taught and lays flat in cord recess.
- Carefully replace the back door. Insure the “latches” on all four corners of the door are lined up, then press the door securely into place.
- Mark the location for the two mounting holes on the wall spaced vertically 2 5/8″ apart.
- If you are mounting the alarm in plaster board or drywall, drill a 3/16″ hole into the wall and insert the plastic anchors provided.
Install the two screws provided into the wall or wall anchors until the screw head is approximately 1/8″ from the wall.
- Hook the unit over the screw head and into the key-hole in back of the unit.
- Plug the adapter into an unswitched wall socket.
Table Top Alarm
You can use your Kidde CO alarm as a table top unit. Follow steps 1 thru 3 above. Instead of mounting the unit to a wall, pull out the slide support and place in a location that is easily visible. Be sure the alarm is no more than three feet from the floor.The alarm does not have to be within three feet from the floor to detect CO, but at this height it is less likely to sustain damage from a fall.
Important Labels Provided
Two labels have been provided that have important information on what to do in case of an alarm. Add the phone number of your emergency service provider in the space provided. Place one label next to the alarm after it is mounted, and one label near a fresh air source such as a door or window.
Carbon Monoxide Alarm Indicator
When the alarm senses a dangerous level of CO, the unit will emit a loud alarm pattern. The alarm pattern is 4 quick beeps followed by 5 seconds of silence. This cycle repeats as long as a dangerous CO condi-tions exist. The red Alarm LED will flash the same pattern (and the PPM will be displayed on alarms with digital displays).
! WARNING: When powered by battery backup only; after four min-utes, the alarm will sound and flash only once every minute, until the alarm is reset or the CO is eliminated.
If the battery is low or missing, or if the unit malfunctions, it will display other readings (and alarm differently) to alert you of specific conditions. Please familiarize yourself, and other family members, to the difference between a CO reading and an indication signifying a problem with the unit itself.
! WARNING: If at any time you test the alarm and it does not perform as described, have it replaced immediately.
Model KN-COPP-3 Operating Characteristics
Whenever the alarm is operating, the digital display will display “0” to indicate the unit is monitoring for CO. If the alarm senses dangerous lev-els of CO, the digital display will indicate the CO concentration in parts per million (PPM), and the alarm will emit an audible alarm pattern. This alarm will display a “0” if CO concentrations between 0 and 30 PPM have been detected within the last 15 seconds. When the unit is first powered up, the digital display will show three “eights” – indicating the alarm is in the start-up mode. The three “eights” will remain for approximately 20 seconds. After 20 seconds, the alarm should display “0” and begin monitoring the air for CO and will continue to do so as long as it receives power. The following table illustrates the possible digital displays, describes the audible alarm patterns, and the recommended actions to take.
Operating and Alarm Characteristics
Model KN-COPP-3 Operating Characteristics
Peak Level Memory
When the Peak Level button is pressed and held, the display shows the highest CO reading taken by the CO alarm since its last reset or power up. The Peak Level display feature will display levels between 11-999 PPM. Although the Peak Level feature will display levels below 30 PPM, these levels will not result in an alarm no matter how long the device is exposed to these levels. The Peak Level feature is helpful in identifying if you have had a CO reading since resetting the alarm.
Concentrations of CO between 1 and 30 PPM can often occur in nor-mal, everyday conditions. Concentrations of CO below 30 PPM may be an indication of a transient condition that may appear today and never reappear. Some CO conditions may start out as low level leaks but could develop into CO concentrations that may become harmful.
Peak Level Memory Reset
Press the Peak Level button; with the button still pressed, press the Test/Reset button for two seconds and release. The number on the dis-play will turn to “0”, the memory will be cleared and the alarm will begin monitoring for CO. The Peak Level memory is also reset when the unit loses power.
NOTE: This unit is sealed. The cover is not removable.
Due to the loudness of the alarm, we suggest that you place your fingers over the sounder opening while testing your alarm.
Caution: Continuous exposure to the high sound level of this alarm over an extended period of time may cause hearing loss.
To test the alarm, press the Test/Reset button. If the unit is operating properly, you will hear 4 quick beeps – followed by 5 seconds of silence – followed by 4 quick beeps. The display will show three “eights” and then show a number – usually around 200). Within several seconds the unit will return to monitor for CO.
Note: You do not need to press the Test button to take a CO read-ing.
NOTE: This CO alarm is not battery operated. However, these alarms are equipped with 9 volt battery backup – the 9 volt battery is to supply short term back-up during a power outage.
When replacing the battery, use one of the following approved brands:
- Duracell MN1604 or MX1604
- Energizer 522
- Gold Peak GP1604A
These batteries can be purchased where you bought the alarm or at a local hardware store. Use of a different battery may have a detrimental effect on the alarm operation.
The 9 volt battery is not rechargeable. If the 9 volt battery is missing, disconnected, or if the battery’s power is low, “Lb” will be displayed alternately with the current CO reading once every second accompanied by an audible beep every 15 seconds. If this happens, the battery must be replaced.
To replace the battery:
Remove back door by sliding it down and out. Remove battery by unsnapping it from the battery clip. Do not disconnect the battery by pulling the battery with one hand and the alarm with the other, as this may break the wires connecting the battery to the CO alarm and void the warranty. Install a new battery by connecting it to the battery clip and place into the recessed battery cavity. Reinstall the back door of the unit.
IMPORTANT: Constant exposures to high or low humidity may reduce battery life. A good safety measure is to replace the battery at least once a year, or at the same time as you change your clocks for daylight saving time.
After installing or changing the battery, reinstall your alarm. Test your alarm by using the Test/Reset button and check that the display is on.
To keep your alarm in good working order, you must follow these steps:
- Test the alarm once a week by pressing the Test/Reset button.
- Vacuum the alarm cover once a month to remove accumulated dust.
- Never use detergents or solvents to clean the alarm. Chemicals can permanently damage or temporarily contaminate the sensor.
- Avoid spraying air fresheners, hair spray, paint or other aerosols near the alarm.
- Do not paint the unit. Paint will seal the vents and interfere with proper sensor operation.
Move the CO Alarm to a remote location, to prevent possible damage or contamination of the sensor, prior to performing any of the following:
- Staining or stripping floors or furniture, painting or wall-papering
- Using aerosols or adhesives
WARNING: Reinstall the CO Alarm as soon as possible to assure co!ntinuous protection.
The following is a list of substances that at high levels can damage the sensor or cause temporary readings that are not CO readings:
- Ethylene, ethanol, alcohol, iso-propanol, benzene, toluene, ethyl acetate, hydrogen, hydrogen sulfide and sulfur dioxide.
- Also most aerosol sprays, alcohol based products, paint, thinner, sol-vent, adhesive, hair spray, after shave, perfume, auto exhaust (cold start) and some cleaning agents.
End of Life Notification
Ten (10) years after unit is first powered, this alarm will beep two times every 30 seconds to indicate it is time to replace the alarm, and “End” will show in the digital display. Once the unit is in End of Life Notification mode, the alarm will no longer detect the presence of CO.
FCC COMPLIANCE STATEMENT
This equipment has been tested and found to comply with the limits for a Class B digital device, pursuant to part 15 of the FCC Rules.
These limits are designed to provide reasonable protection against harm-ful interference in a residential installation. This equipment generates, uses and can radiate radio frequency energy and, if not installed and used in accordance with the instructions, may cause harmful interference to radio communications. However, there is no guarantee that interference will not occur in a particular installation. If this equipment does cause harmful interference to radio or television reception, which can be determined by turning the equipment off and on, the user is encouraged to try to correct the interference by one or more of the following measures:
- Reorient or relocate the receiving antenna.
- Increase the separation between the equipment and receiver.
- Connect the equipment into an outlet on a circuit different from that to which the receiver is connected.
- Consult the dealer or an experienced radio/TV technician for help
TEN YEAR LIMITED WARRANTY
Warranty Coverage: The manufacturer warrants to the original consumer purchaser, that this product (except battery) will be free of defects in material and workmanship for a period of ten (10) years from date of purchase. The manufacturer’s liability hereunder is limited to replacement of the product, repair of the product or replacement of the product with repaired product at the discretion of the manufacturer. This warranty is void if the product has been damaged by accident, unreasonable use, neglect, tampering or other causes not arising from defects in material or workmanship. This warranty extends to the original consumer purchaser of the product only.
Warranty Disclaimers: Any implied warranties arising out of this sale, including but not limited to the implied warranties of description, merchantability and fitness for a particular purpose, are limited in duration to the above warranty period. In no event shall the Manufacturer be liable for loss of use of this product or for any indirect, special, incidental or consequential damages, or costs, or expenses incurred by the consumer or any other user of this product, whether due to a breach of contract, negligence, strict liability in tort or otherwise. The Manufacturer shall have no liability for any personal injury, property damage or any special, incidental, contingent or consequential damage of any kind resulting from gas leakage, fire or explosion. Some states do not allow limitations on how long an implied warranty lasts, so the above limitation may not apply to you. Some states do not allow the exclusion or limitation of consequential or incidental damages, so the above limitations or exclusions may not apply to you.
Legal Remedies: This warranty gives you specific legal rights and you may also have other rights that vary from state to state.
Warranty Performance: During the above warranty period, your product will be replaced with a comparable product if the defective product is returned in a postage paid package to the following address: Kidde, Customer Service Department, 1016 Corporate Park Drive, Mebane, NC 27302 USA, together with proof of purchase date. Please include a note describing the problem when you return the unit. The replacement product will be in warranty for the remainder of the original warranty period or for six months, whichever is longer. Other than the cost of postage, no charge will be made for replacement of the defective product. In many cases the quickest way to exchange your alarm is to return it to the original place of purchase. If you have questions, call Kidde customer service department.
IMPORTANT: Do not remove unit back cover. Back cover removal will void warranty.
Your Kidde Carbon Monoxide Alarm is not a substitute for property, disability, life or other insurance of any kind. Appropriate insurance coverage is your responsibility. Consult your insurance agent.
Also, Kidde makes no warranty, express or implied, written or oral, including that of merchantability or fitness for any particular purpose, with respect to the battery.
The above warranty may not be altered except in writing signed by both parties hereto.
QUESTIONS OR FOR MORE INFORMATION
Call our Product Support Line at 1-800-880-6788 or contact us at our website at www.kidde.com
Documents / Resources
|Kidde KN-COPP-3 Carbon Monoxide Alarm [pdf] User Guide|
KN-COPP-3, Carbon Monoxide Alarm, KN-COPP-3 Carbon Monoxide Alarm