ATE HSIO CARD CAGE – SITE INSTALL
FOR USE WITH ADVANTEST V93000 CTH AND STH TESTERS
This document is used to install the Multilane (ML) High Speed I/O option at the customer site. The only additional site resource required by ML is the Site Utility Air Supply. All other resources and connections are made between the Multilane option and the existing V93000 tester cell. This installation manual assumes the Multilane software and customer test programs are properly installed on the V93000 workstation. You are only installing the hardware with the help of this manual.
Applicable Multilane Documents
- Site Preparation manual
- Utility Box manual
- System manual
- Diagnostics manual
Making System Connections
- Connect “air input” air cable assembly
a. Connect air cable between site utility air supply and Utility box
b. Site Utility Air Air Input in Figure 3: Utility Box Inputs/Outputs.
- Connect “V93000 power” cable
a. Connect power cable between STH/CTH location and Utility box power input
b. If V93000 is STH, then refer to Figure 9: V93000 STH power switched outlets.
c. If V93000 is CTH, then refer to Figure 8: V93000 CTH power switched outlet.
d. STH/CTH Power Power Input in Figure 3: Utility Box Inputs/Outputs.
- Connect “Workstation Ethernet” cable
a. Connect Ethernet cable between V93000 workstation and Utility box LAN input
b. Refer to V93000 manual for ethernet cable connection
c. V93000 Ethernet LAN input in Figure 3: Utility Box Inputs/Outputs.
- Connect “air output” air cable assembly
a. Open Air door of utility box. Feed air tube into air regulator output and out of top of utility box
b. Air Cable from utility box Air Supply Input in Figure 7: Twinning Frame Faceplate.
- Connect “LAN outputs”
a. Connect 2 Ethernet cables between the utility box and the twinning frame
b. Each ethernet cable can plug into either LAN connection
c. Utility Box LAN outputs LAN Connections in Figure 7: Twinning Frame Faceplate.
- Connect “Power output”
a. Connect power cable between the utility box and the twinning frame
b. Utility Box Power outputs +12V Power Input in Figure 7: Twinning Frame Faceplate
- Tie wrap the cables going between the utility box and twinning frame
a. Air supply, power cable, ethernet cables
Checking System Connections
- Check system air
a. Turn on utility box air. See ballcock valve in Figure 7: Twinning Frame Faceplate.
b. Using air regulator inside utility box, set CFM to be 3 CFM¹
c. Listen for air exiting into Multilane twinning frame
- Check system power
a. Turn on V93000 power → Note utility box power input LED is ON
b. Manually turn on twinning frame power via toggle switch located on utility box → Note utility box +12V power LED is ON
c. Power toggle switch and power on LED are shown in Figure 4: Utility Box Buttons and LED Indicators
- Check LAN connection
a. Note ethernet IP addresses of each Multilane instrument inside the card cage
b. For each IP address, PING the IP address and verify a PING response is returned
- Run Multilane loopback diagnostics
¹ Check with Multilane for CFM requirements for customized instruments
Multilane Recommended Utility Box Site Location
MultiLane Regional Locations
48521 Warm Springs Blvd, Suite 310
Fremont, CA 94539, ԱՄՆ
+1 510 573 6388
Europe, South Asia
Houmal Technology Park
Askarieh Main Road
+961 81 794 455
14F-5/ Rm.5, 14F., No 295
Sec.2, Guangfu Rd. East Dist.
Hsinchu City 300, Taiwan (R.O.C)
+886 3 5744 59
Փաստաթղթեր / ռեսուրսներ
|multiLane V93000 Ate Hsio Card Cage [pdf] Օգտագործողի ձեռնարկ|
V93000 Ate Hsio Card Cage, V93000, Ate Hsio Card Cage, Card Cage, Cage