TH4110U2005/U TH4210U2002/U Wiring Diagrams [pdf]: T4 and T1 PRO Wiring Diagrams Specifications T4 Pro Programmable Thermostat Color White…
This is a legacy product document supported by Resideo. It is no longer manufactured
This manual covers the following models:
TH1100D, TH1110D and TH1210D non-programmable thermostats
TH1110D and TH2110D:
TH2110D and TH2210D
TH1210D and TH2210D:
Must be installed by a trained, experienced technician
Read these instructions carefully. Failure to follow these instructions can damage the product or cause a hazardous condition.
For assistance with this product please visit http://yourhome.honeywell.com or call Honeywell Customer Care toll-free at 1-800-468-1502.
Can cause electrical shock or equipment damage. Disconnect power before beginning installation.
If this product is replacing a control that contains mercury in a sealed tube, do not place the old control in the trash. Contact your local waste management authority for instructions regarding recycling and proper disposal.
Gas, oil or electric heating (1H)
Gas, oil or electric heating and/or air conditioning (1H / 1C / 1H1C)
NOTE: This setting is necessary only if the thermostat is connected to a heat pump.
The jumper is located on the back of the thermostat faceplate. Set it according to the type of reversing (changeover) valve used by the heat pump.
NOTE: This setting is not applicable if a fan is not connected to the G terminal.
A jumper, located on the back of the thermostat faceplate, determines how the fan operates in Automatic mode. This jumper is not available on TH1100, TH1210D and TH2210D. On the TH1210D and TH2210D models, when the fan is placed in Automatic mode, it starts right away when there is a call for heat or cool.
Incorrect jumper setting: An incorrect setting is noticeable in a gas or oil heating system.
When heating starts, you will initially feel cold air coming out of the vents as the fan is running before the furnace has enough time to heat up the air.
If a 24-VAC common wire is connected to the C terminal, batteries are optional and serve to provide backup power.
If a 24-VAC common wire is not connected to the C terminal, batteries are necessary to power the thermostat.
Install 2 AAA batteries on the back of the thermostat faceplate as shown.
Follow the procedure below to personalize and configure the thermostat according to the heating/ cooling system.
NOTE: If you do not press any button for 60 seconds while you are in the setup menu, the thermostat automatically saves any changes made and exits the menu. For programmable models only, at any time you can save the changes and exit by pressing the Run button.
|1 Temperature display format||0||0: Fahrenheit 1: Celsius|
|2 Time display format||0||0: 12-hour display 1: 24-hour display|
|3 Heating cycles per hour||5||2 to 6 cycles per hour |
•2: 30 min (steam, gravity)
•3: 20 min (hot water, 90%+ high-efficiency furnace)
•4: 15 min (gas or oil)
•5: 12 min (gas or oil)
•6: 10 min (electric)
|4 Cooling cycles per hour||3||2 to 6 cycles per hour|
|5 Compressor protection2||1||0: Off |
|6 Adaptive Intelligent Recovery3||1||0: Off |
|7 Application4||0||0: Indoor mode: 40°F to 90°F (4.5°C to 32°C) 1: Garage mode: 35°F to 90°F (1.5°C to 32°C)|
PRO 1000 / 2000 Series
Programmable and Non-programmable Thermostats
|Honeywell PRO 100 Programmable and Non-programmable Thermostats [pdf] Instruction Manual|
PRO 100, PRO 200, Programmable and Non-programmable Thermostats
Technical Pro USB and SD Card Inputs Stereo Speakers Specifications DIMENSIONS: 20.75 x 19 x…
RS141B LED Spot Coreline light source of energy efficiency class E E © 2018 Signify…
1850 M2 Vessel Systems Monitor Instructions M2 Vessel Systems Monitor (M2-VSM) PN 1850 Installation Checklist…
Dash Aircrisp Pro Digital Air Fryer DMAF360 User Manual [ Download Recipe Guide PDF ]…
Toshiba TLP-S10U LCD Mobile Video Projector