Honeywell BW Icon Portable Multiple Gas Detector User Guide Introduction The Honeywell BW™ Icon & BW™ Icon + gas…
The following instructions cover installation and wiring the BW RigRat I.S. Barrier. This equipment should only be connected in accordance with applicable regulations by qualified personnel.
The equipment is intended for association in accordance with intrinsic safety; the installation mustbe in compliance with standard EN 60079-14, in particular paragraph 12.
The equipment is intended for installation on an EN 50022 rail attached horizontally on a vertical plane, in order to respect the direction of natural convection
Do not obstruct the air vents. Use a screwdriver to insert and remove the equipment as indicated
The equipment must be installed in a non-explosive atmosphere, in a safe environment free of condensation and corrosive or conductive dust. Intrinsic safety is ensured in the operating temperature range specified in paragraph 1.6. However, you should remember that the service life of electronic equipment is reduced by half when its temperature is increased by 10° C. You should therefore install the equipment in suitably ventilated equipment rooms, avoid the proximity of elements that may heat the equipment by radiation or which are likely to generate electromagnetic radiation greater than 10V/m.
Electrical connections must be made when the equipment is DE-ENERGIZED, using wires with a maximum diameter of 2.5 mm2. For connections, refer to the wiring diagram
The intrinsic safety terminals must only be connected to intrinsic safety equipment or equipment that is in compliance with paragraph 5.7 of standard EN 60079-11. Moreover, the association of equipment and the connection cable must be compatible in terms of intrinsic safety.
The properties of cables and their routing from the ATEX zone (I.S. cables) must comply with the recommendations set out in paragraphs 6.1, 6.2.1 and 6.3 of standard EN 600079-11. Full precautions must be taken to prevent electromagnetic disturbance with other cables that may generate dangerous voltages or currents. The I.S. cables must be clamped in order to prevent random contact with other cables in the event the terminal is cut or damaged.
Adjustments and configuration
See technical data sheet or instructions for use.
Precautions to take during maintenance. Unmounting must be carried out DE-ENERGIZED. In the event you suspect a failure or permanent fault, return the equipment to our services or representatives, who are the only maintenance providers certified to perform expert assessments or repairs.
Un-mount the unit from the enclosure by using a screwdriver as shown:
|Honeywell BW RigRat I.S. Barrier Area Gas Detector [pdf] Installation Guide|
BW RigRat, I.S. Barrier Area Gas Detector, BW RigRat I.S. Barrier Area Gas Detector, Barrier Area Gas Detector, Area Gas Detector, Gas Detector, Detector
305.110.14 BONDTOLVAN Alarm clock BONDTOLVAN 2 134 mm (XX") 1 1 3 © Inter IKEA…
MD03 Pore Purifer Advanced Microdermabrasion Tool Product Information The SKN by Conair Pore Purifier AdvancedTM…
6610-15 8+8 Ports Managed Fiber Ethernet Switch Product Information: The 6610-15 Managed Fiber Ethernet Switch…
IXV Ti Keychain Flashlight Product Information Model: IXV Ti Specifications: High-180 lumens, Low-5 lumens, 580cd,…
EBT1-22090 TWS Fashion Pro Earbuds FCC I D: 2AS5O- EBT1- 22090
JZ10082 Stackable 2-Drawer Horizontal Organizer Product Information: The product is identified by the code JZ10082…